Disasters: Air-conditioning (IV) Monday 10 th incident believed to be caused by a planned reboot of the Building Management System (BMS) –Caused pumps to stop –Low pressure caused chiller valves to close –BMS returned but system deadlocked Tuesday 11 th – single chiller trip followed by failover –logs do not allow diagnosis.
{}