Chapter 11 Refrigeration – Part I 1117.0 Overpressure Protection.
{"Image DocumentName": "Chapter 11 Refrigeration \u2013 Part I", "Image ImageDescription": "Overpressure Protection General. Pressure vessels shall be provided with overpressure protection as required by this section Type of Protection. Pressure vessels with three (3) cubic feet (0.085 m3) internal gross volume or less may use a single pressure-relief device or a fusible plug. Pressure vessels over three (3) cubic feet (0.085 m3) but less than ten (10) cubic feet (0.283 m3) internal gross volume may use a single pressure- relief device but not a fusible plug. Pressure vessels of ten (10) cubic feet (0.283 m3) or more internal gross volume shall use a single rupture member or dual pressure-relief valve. LANES POINTS.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}