Fault loop impedance c) The path through the neutral point of the transformer and the transformer winding. d) The active conductors as far as the poin
{"Image DocumentName": "Fault loop impedancec) The path through the neutral point of the transformer and the transformer winding.", "Image ImageDescription": "d) The active conductors as far as the point of the fault. The earth fault-loop is normally regarded as consisting of the following two parts- i) conductors upstream or external to the reference point; and. ii) conductors down stream or internal to the reference point. Refer to appendix B for detail.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}