New Albany, OH - Upon arrival found condenser not operational, Noticed hard start kit has blown up, did not have a hard start kit on truck to replace, Removed bad hard start kit at customer's request, system kicked on operational, checked inrush amps on compressor and had 12.3amp max amps is rated at 17.9, checked pressures all is good,
{}