This document is intended to assist licensed professionals in the exercise of their professional judgment.  2011 Addison Standard Cycling Hot Gas Reh
{"Image DocumentName": "Standard Cycling Hot Gas Reheat", "Image ImageDescription": "Show hot gas reheat being fed from the top discharge line from the compressor. The reheat solenoid is controlled by a reheat thermostat located in the blower discharge. The Varispeed head pressure control maintains the head pressure when the unit goes in and out of reheat. The hot gas bypass is activated by low suction pressure. K is the Addison drain for liquid refrigerant in the reheat coil. The liquid line pump down solenoid is only used on long refrigerant line applications.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}