Huber Heights, OH - Customer advised had another company out the previous day. She was told she was low on refrigerant and needed new compressor. Outdoor unit was attached to frame and suspended to the house  The bracket is broken and the unit was approximately 8 inches from Being level.Was able to brace the bracket and system bringing it back to level. System was turned on and pressures checked. Pressures were well within manufactures specs. Recommend having unit moved to ground level.
{}