Fault loop impedance The earth fault-loop impedance in an MEN system comprises the following parts, starting and ending at the point of the fault. a)
{"Image DocumentName": "Fault loop impedanceThe earth fault-loop impedance in an MEN system comprises the following parts, starting and ending at the point of the fault.", "Image ImageDescription": "a) The protective earthing conductor, (PE), including the main earthing terminal/connection or bar and MEN. b) The neutral return path, consisting of the neutral conductor, (N), between the main neutral terminal or bar and the point at the transformer (the earth return path RG to RB has a relatively high resistance and may be ignored for an individual installation in an MEN system)", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}