Washington, PA - Responded to an after hours no heating call, in an apartment building. Found system off on a low water cut out fault. Traced the piping, and opened the main water line. Filled and fired the boiler. Took pictures for the owner, and made repair recomendations.
{"Image Orientation": "Horizontal (normal)", "Image ExifOffset": "38", "EXIF ColorSpace": "sRGB", "EXIF ExifImageWidth": "960", "EXIF ExifImageLength": "720"}